The 1494G-BF3J6-98-412-414 enclosed disconnect safety switch is manufactured by Allen-Bradley/Rockwell Automation in the Industrial Safety Disconnect Switches product line and it belongs to the Bulletin 1494 device family with a standard size enclosure current rating of 30 to 600 Amps and a switch rating of 30 Amps. It has the NEMA Type 3R/4/12 enclosure type, which is watertight, rainproof, dust-tight, has a non-metallic handle, and also has a painted metal enclosure with screw fasteners. The Allen-Bradley 1494G-BF3J6-98-412-414 switch is a three-phase and three-pole switch, and it belongs to the Class J fusing category with a fuse voltage of 600 Volts AC or 600 Volts DC. It also comes with factory-installed options including a N.O. auxiliary disconnect, a painted metal handle, and a protective fuse cover. Some of the main features of this disconnect switch include a lockable handle, a standard non-metallic handle with 30 to 200 Amps of current, and a visible blade construction to enhance safety.
The Allen-Bradley 1494G-BF3J6-98-412-414 Disconnect Switch has switch ratings of 30 to 100 Amps in extra-capacity enclosures. It is also linked to the handle at all times and has an optional stainless steel or metal handle with field-installed accessories as well as factory-installed options. It is listed and rated for compliance with the UL 98, CSA C22.2, and UL 508 standards. Some of the notable accessories of this switch include protective fuse covers, protective line covers, a terminal lug adapter kit, ground adapters, and non-metallic conduit connectors. Other specifications of the 1494G-BF3J6-98-412-414 switch include a low-level switching current of 5 milliamps at 12 Volts DC. It operates at a temperature ranging between -35 and 40 degrees Celsius and it has a storage temperature ranging between -40 and 65 degrees Celsius.
Repair Services for 1494G-BF3J6-98-412-414
||$425.50||Add to Cart |
Our highly skilled technicians can repair your 1494G-BF3J6-98-412-414. All of our repairs come with a 1 Year DO Supply Warranty. Please contact us for additional information about our repair process.