The 193-EC1PB relay is an overload relay unit by Allen-Bradley/Rockwell Automation. The unit is part of the Bulletin 193-EC product line and it allows communication through the DeviceNet network. The DeviceNet network supports polled I/O messaging, explicit messaging, auto-baud network rate identification, and unconnected message managing. The overload relay has buttons for testing and resetting itself, along with status indicators that are LED lights. The status indicators indicate the network status, that status of closed contacts, warnings, and tripping. Also, the 193-EC1PB overload relay provides protection from underload or undercurrent situation if conditions like tool breakage, belt breakage, or pump cavitation occur. The unit has functions for diagnostics and current monitoring, and several protective functions. The protective functions of the unit include thermal overload, over-temperature, remote trip, current imbalance, phase loss, and ground fault protection.
The Allen-Bradley 193-EC1PB overload relay has an E3 configuration and it features a current adjustment range of 0.4 to 2 Amps. The relay component supports a contactor size of C09 to C23. Like other E3 overload relay units from this product series, it includes 2 inputs and 1 output. The operating frequency range is 20 to 250 Hertz while the rated insulation voltage is 690 Volts AC. The unit meets requirements from all the applicable standards and it includes certifications from the CCC, CE, and the ABS. The 193-EC1PB electronic overload relay dissipates 3.83 Watts of maximum heat and it consumes up to 3.2 Watts of power. The unit has a moderate resistance to shocks and vibrations and it has the 1P1X degree of protection. According to the requirements of the systems operating in industrial environments, the unit is adjusted for typical operating temperatures and conditions.
Repair Services for 193-EC1PB
||$267.97||Add to Cart |
Our highly skilled technicians can repair your 193-EC1PB. All of our repairs come with a 1 Year DO Supply Warranty. Please contact us for additional information about our repair process.