The 40185-802-01 kit is an overload relay kit for size 4 Allen-Bradley starter devices. It has been manufactured by Allen-Bradley/Rockwell Automation. It is compatible with the Allen-Bradley Bulletin 509 line of the NEMA starters. The relay kit is manufactured out of an eutectic alloy material. The relay kit comprises coils and contactors. It also comes with mounting plates and overload devices. The 40185-802-01 overload relay kit has a nylon space insulator that is used alongside the nylon standoff device. A current transformer is present on the lower side of the relay. The starter devices are used for the full voltage starting of the polyphase squirrel cage motors. These starters meet the NEMA standards and they are easy to use.
The 40185-802-01 overload relay kit should be installed in a suitable enclosure for protection. The motor should be disconnected from the mains during installation. This eutectic overload relay comes with a test module on the right side, that helps to open the closed overload contacts for test purposes without tripping the relay. The overload relay can be removed by using a screwdriver. The blade of the relay should be vertically held and inserted during the removal process. The 40185-802-01 kit is connected to the block and the base assembly, mounting plate, and load lines. The relay is mounted by using mounting screws with washers. The overload relay kit is a 3-pole unit with an open enclosure. The relay unit is used with motors with a voltage rating of 120 to 600 Volts AC. It has a 7200 Volts-Amps rating and it has a brake rating of 720 Volts-Amps. The ambient temperature should not exceed 70 degrees Celsius.
Repair Services for 40185-802-01
||Ask|| Get Quote |
Our highly skilled technicians can repair your 40185-802-01. All of our repairs come with a 1 Year DO Supply Warranty. Please contact us for additional information about our repair process.