Description: Allen Bradley-COMMUNICATION MODULE PLC
|Warranty:||1 year DO Supply Warranty Included|
|Shipping:||Worldwide shipping via DHL, UPS, Fedex, and TNT|
|Repairs:||We offer repair service for the 1794-AV-MVI.|
|Exchange:||Exchange credit for your defective unit available.|
To Speak to a sales representative for pricing & lead time:
The 1794-AV-MVI is an adapter module for the 1794 Flex I/O terminal modules. The 1794 modules are designed to be operated in a pollution degree 2 industrial environment and it complies with the NEMA standards 250 and the IEC 60529 as applicable. The 1794-AV-MVI should be installed or removed only when the back panel power is turned off. If the users remove the module when the power is on, an electric arc may occur. The module should be operated at an ambient temperature of 0 to 55 degrees Celsius and the relative humidity must between 5 and 95%. Make sure the connections are made according to the instructions in the manual and that the connections are secured and install only a single wire in a single port. Tighten the screw securely to avoid any loose connections.
It is also recommended to prevent any electrostatic discharge because it may cause internal damage to the 1794-AV-MVI. Users should touch a grounded object before touching the equipment to discharge any static electricity. Users should also wear an approved ESD strap while handling the equipment and use a static-safe workstation if available. When the power is turned on, the terminal unit should not be removed and all the safety instructions must be followed when installing the module. The 1794-AV-MVI has a capacity for supporting 8 modules and it is mountable on a DIN rail. It operates on an input voltage of 24 Volts DC. When installing the adapter, make sure the hook on the terminal base is under the adapter and the connector is fully retracted, then slide the terminal base over tightly against the adapter.
|Module Type:||Adapter Module|
|Module Capacity:||8 Modules|